Emerging Voltage Drop Solution Saves Grid Operator \$9.4Million in cable costs

13 Sep 2021

“What is voltage drop? How do I calculate it? And why does it cost a fortune to solve this problem!?”

In most electrical design processes, overcoming this problem can be an extremely costly affair.

The goal is to satisfy the maximum allowable voltage drop in the electrical system, no matter the size of the load.

Yet the existing solutions to long-distance cable runs are causing a significant dent in project budgets.

So if you’re looking for practical ways to finally put an end to your voltage drop woes…

You’re in the right place.

In this article, we reveal our “No BS”, field-tested methodologies on how you can successfully eliminate voltage drop, for good.

To kickstart your journey, it is crucial to first understand the what’s and how’s of voltage drop.

Let’s get started.

What Is Voltage Drop?

A voltage drop in an electrical circuit typically occurs when a current passes through the cable.

It is related to the resistance or impedance to current flow with passive elements in the circuits including cables, contacts and connectors affecting the level of voltage drip.

So the longer the length of the cable (or circuit), the greater the voltage loss.

Let’s take a look at this simple, step-by-step method to calculate your voltage drop.

Step 1: Take the value from the volt drop table (mV/A/m)

Step 2: Multiply the ACTUAL current in the cable (NOT the current rating)

Step 3: Multiply by the length of run in METRES.

Step 4: Divide results by 1,000 (to convert millivolts to volts)

Here’s an example of how the formula works – just for you:
Voltage drop (VD) = (mV/A/m x I x L) / 1000)
or

Voltage drop (VD) = (Step 1 x Step 2 x Step 3) / Step 4)

Think of the water that flows out of a tap and then down a long hose.

The farther away you get from the tap, the weaker the stream of water will be that flows out of it.

The same is true of electricity through wires:

“The farther the electricity gets from the source, the weaker the current will be.”

So now that we have a better understanding, let’s deep dive into more details.

Having trouble with Voltage Anomalies? Get in touch with us at sales@ashleyedison.com.

Maximum Voltage Drop Allowed In Australia

In most parts of Australia, the nominal single phase supply voltage is 230 volts +/- 6%, this represents a range between 216.2 and 243.8 volts. (With the exception of Western Australia remaining at a nominal voltage of 240V +/- 6%).

As specified in clause 3.6.2 of AS/NZS 3000:2018 on standard installations, the maximum permissible voltage fall between the point of supply and any point of the installation is as follows:

Here’s a Rule of Thumb.

The following voltage drop limits can be used as a guide to assist with design:

In the electrical world where the threat of voltage drop is persistent and inherent.

These problems can also cause total distress to engineers.

So, this leads us to a very important question…

What is the negative impact on your equipment?
(
The consequences will shock you…)

Disastrous Consequences Of Voltage Drop

Industry studies show that a 20% voltage drop lasting just 50 seconds can be extremely detrimental to your equipment’s health.

The outcomes can vary from horrifying equipment malfunction to complete facility downtime.

Here are 9 harmful consequences of voltage drop:

These undesirable problems can post a challenge to electrical engineers.

But what exactly causes voltage fall to happen?

Let’s find out below.

What Causes Voltage Drop?

You may want to sit up for this.

Common challenges when trying to eliminate voltage drop, is the lack of understanding of what causes it.

In an environment with no room for mistakes, engineers leave nothing to chance. No guesswork, no trial and error.

Here are the 6 determining factors that cause voltage drop to happen:

Now that you have a better understanding of all the primary conditions that cause voltage drop.

You would be wondering.

How Can I Minimise Voltage Drop?

Well, your search is finally over.

There are basically 2 ways of overcoming this issue:

1. Conventional ways of minimising voltage drop.
2. Adaptive way to eliminate and save.

Let’s investigate..

#1. Conventional ways of minimising voltage drop.

These methods have been the default solutions for minimising excessive voltage drop:

1. Compensating voltage drop using larger cross-sectional sized cables. This offers less resistance / impedance to current flow.
2. In power distribution systems, a given amount of power can be transmitted with less voltage drop if a higher voltage is used.
3. Increasing the quantity of the cables will decrease the resistance – causing voltage drop to decrease, and increase your overall efficiency. (This will also lower overall power loss!)

If you’re at the preliminary design stage of your project, you may find that the costs involved in these conventional methods will make a significant dent in your budgets…

And that’s how some processes come to a screeching halt.

On the other hand, ensuring a regulated and stabilised voltage supply should always be a priority.

After all, the failure of your system’s assets is the very risk that must be mitigated if not eliminated..

#2. Adaptive way to eliminate and save.

So how are grid operators and consultants effectively eliminating voltage drop, saving millions on cable cost?

Case Study

(2017 Underground Transmission Cable Tunnel Project)

• Distance Between Point Of Supply And Point Of Installation: 7.4 km
Max Design Current: 134.33 A
• Point Of Supply: 500V
• Desired Voltage Value At Point Of Installation: 400V
• Cables Used: XLPE / SWA / PVC / Armoured Cables

In efforts to sustain the reliability and security of electricity networks, a Grid Operator completes a \$2.4-billion project, spanning a 40km network of three tunnels built to house 1,200m of transmission cables.

The objective was to ensure voltage values at the load end were kept within the maximum allowable voltage drop levels at 4% of 400/230V (376V / 216.2V).

However, in just one portion of the project alone, the original electrical design utilising conventional methods of increasing the quantity and sizing of cables:

Would have amounted to an estimated \$12 million in cable costs..

What was required to overcome the key issue of voltage drop and high cable costs – was a solution that is efficient and cost-effective:

And in 2017, Ashley-Edison’s Automatic Voltage Regulators were deployed to:

• Boost low voltage levels at every load end of the cable tunnel.
• Regulate and maintain an optimum output voltage, even if the load changes.

Through a carefully designed configuration, over a dozen Automatic Voltage Regulators have helped achieve the objectives and save over \$9 million dollars in project budget.

These savings solely came from what would have otherwise been spent on cabling costs.

In Conclusion

The key to effectively eliminate voltage drop problems is essentially having a solution that is both on point, and on budget.

If you need help solving your voltage problems or you wish to explore more innovative ways to optimise your electrical system, let our expertise be your guide.

Are you a firm believer of conventional engineering methodologies?

Are you against the idea of other field-tested alternatives to solve your power problems?

P.S. Want to know how other esteemed companies are overcoming their power problems?

Scroll to Top
Thank you for getting in touch with us.

We will be in contact shortly.

Three Phase

SESL-H-3P-S Model
Large Capacity Rating
200 to 2,000 KVA

 Enclosure 335 1000W x 1300H x 580D (mm) 250~300 KVA ± 15% 120~200 KVA ± 20%

 Enclosure 336 1280W x 1480H x 660D (mm) 400 KVA ± 15% 250 KVA ± 20%

 Enclosure 337H 1880W x 1950H x 880D (mm) 500 KVA ± 15% 300 KVA ± 20%

 Enclosure 339 1470W x 1950H x 1340D (mm) 600 ~ 1,500 KVA ± 15% 400 ~ 1,000 KVA ± 20% 300 ~ 750 KVA ± 25% 300 ~ 600 KVA ± 30%

Three Phase

SES-H-3P-S Model
60 to 1,000 KVA

 Enclosure 333 490W x 800H x 990D (mm) ≤ 100 KVA ± 15%

 Enclosure 334 540W x 900H x 1000D (mm) 120 – 150 KVA ± 15%

 Enclosure 335 1000W x 1300H x 580D (mm) 180 – 300 KVA ± 15% 120 – 200 KVA ± 20% 120 – 150 KVA ± 25%

 Enclosure 336H 1880W x 1480H x 660D (mm) 400 KVA ± 15% 250 KVA ± 20% 180 ~ 200 KVA ± 25%

 Enclosure 337H 1880W x 1950H x 880D (mm) 500 KVA ± 15% 300 KVA ± 20% 250 KVA ± 25%

 Enclosure 339H 2170W x 1950H x 1340D (mm) 600~1,000 KVA ± 15% 400~600 KVA ± 20% 300~400 KVA ± 25%

SES-H-S Model